Relays and Relay Enclosures
Relays and Relay Enclosures
Use these Relays to connect devices for use with the ISIMET Utility Controller. Enclosures are available with relay with (Model # IEx-R-S).
When ordering replace x with the number of relays needed in the enclosure.
Resets are sized to meet amperage requirements of the Connected solenoid.
IE1 5 X 5 X 3 Enclosure
IE2 5 X 7 X 4 Enclosure
IE1-R-S Single Relay Enclosure
IE2-R-S Dual Relay Enclosure
IE3-R-S Three Relay Enclosure
I-SR1 Single Relay w/o Switch
I-SR2 Single Relay w/ Switch
IRE1 Single Solenoid Reset Enclosure
IRE2 Dual Solenoid Reset Enclosure
Model RIBMN24C (less switch) or RIBMN24S (with switch)
Coil Voltage Input 24-vac / dc; 50-60 Hz
Operating Temperature -30 to 140° F
Dimensions 1.1” X 2.75” X 1.75”
Approvals UL Listed, UL916, UL864, C-UL Canada
470 VA Pilot Duty 120-240 vac
Drop Out = 3-vac / 3.8-vdc
Pull In = 20-vac / 20-vdc
Junction boxes are recommended for uses in accessible areas, such as control panels and enclosures, and concealed areas, such as ceiling spaces, in order to accommodate control wiring connections between the various components of the system.
Caution: Only connect 24 vac control wiring from Utility Controller output circuits to input posts at relay terminal for 120 vac coil voltage devices as shown with Model # RIBMN24C panel mounted relay.
Caution: Only connect 24 vac control wiring from Utility Controller output circuits to input wire leads for 24 vac devices.
ISIMET Utility Controllers and Companion Enclosures
Two Hour Fire Rating
UL Test #1479
All ISIMET Utility Controllers, Enclosures and Accessories can be certified for two-hour fire rating. Working closely with the industry leader in fire rated materials, ISIMET can offer our enclosures with a one-half inch fire rated blanket. This blanket that is adhered to the outer surface of the enclosure will enable the installer to incorporate the ISIMET product into a fire rated wall without the need for additional blanket or other rated material.
To specify a unit as “Fire Rated” use the following nomenclature:
Add to the ISIMET Part Number: Prefix “F2” for all Utility Controllers, Companion Enclosures and Accessories. Model numbers are for example only.
UtC-F2-12X9 indicates a four-circuit Utility Controller with fire blanket.
LA-F2-1212 indicates a wall mounted LA Series with fire blanket.
FLA-F2-2235 indicates a wall mounted FLA Series with fire blanket.
E-F2-1212 indicates a twelve-circuit E-Series with fire blanket.
S-F2-1211-3-3/4-K indicates a three-station S-Series with fire blanket.
MLA-F2-1-B indicates a Monitoring Beacon with fire blanket.
All components utilized in this “Fire Rating” will be provided with additional instructions for installation in order to insure that the rated material and process is not violated or damaged during installation. Fire caulking as well as foil tape and extra blanket material is included for all components except for accessories. Accessories are provided with foil tap and extra blanket only. Fire caulking will need to be field provided. Enclosure Sizes limited to 24” X 24” X 8” and smaller.
|Fire Rating||Field Instructions|